- Hot Featured Generators
- Land Diesel Generator Set
- Marine Diesel Generator Set
- Gas Engine Generator Set
- HFO Power Generator
- Dual Fuel Power Generator
Overseas Market Sales Dep.
Add: No.188, Anshan West Road,
Tianjin, China 300071
Skype No 1: ettespower
Skype No 2: ettesgenerator
After Sales Service:
Generator Control System
For emergency power in buildings, Auto Transfer System (ATS) is essential. ATS can automatically transfer load from main power to emergency power without operators operation. When the main power fails or voltage drop below 80% of normal voltage, the ATS will start emergency generator set after a preset time from 0 to 10 seconds (Adjustable). At rated speed, the ATS will transfer load to emergency power with available from 40A to 4,000A. There is a SWT ATS that can meet every project's need.
1). With an industry class MPU as the kernel, handles across-the-board, monitors the voltage and Frequency of main power
2). SOCOMEC (France)or Chinese 4 poles auto transfer switch, with electrical and mechanical Interlock mechanism.
3). Good quality, good appearance
4). Long life and liable LED pilot lamp
5). Separate panel or built-in panel (mounted in generating set Control panel)
6). About how to configure ATS current?
When the prime power of the generator set is X, then "CURRENT Value≥2X",eg. Prime=220 Kw, the ATS Current should be ATS-500 (500A)
Parallel Synchronizing Control Panels
1). Paralleling conditions:
a) Generator sets should be equipped with electrical governor system
b) Incoming genset phase sequence must be same as main power
c) Voltage difference is in the limit between genset and main power
d) Frequency difference is in the limit between genset and main power
e) Phase angle difference is in the limit between genset and main power
2). Better reliability and continuity of electrical power:
The paralleling of generator sets enhances system performance because they can stand much more load than one genset do
3). Convenient maintenance and service:
With generator sets operated in paralleling system, servicing generator sets will not interrupt emergency power to critical system
4). More economic:
Operator can manage the operating gensets according main power load. It eliminates the waste of fuel and lubrication oil while bigger power genset carry smaller load
5). More flexibility for future expansion:
Paralleling system offer economy of installing only as much power as you need, then adding generator set as building power expands.